Product Thermal Capacity: 1 - 20 t/h
Working Pressure: 0.7 - 2 Mpa
Available Fuel: Nature gas, coke oven gas, biogas, methanol, liquid propane gas, diesel, heavy oil, light oil, crude oil, etc.
Available Industries: Heat supplying, chemical, food, textile, printing and dyeing, cigarettes and tobacco, fodder, pharmacy, building materials, brewery, rubber, hospital etc.
WNS series horizontal internal combustion boiler is a boiler shell type 3 passes wetback oil/gas fired boiler. After fuel is being atomized by burner, flame is full of the wave furnace and transfer heat via furnace wall, this is 1st pass; the high temperature smoke is collected in reversal chamber and then enters 2nd pass which is grooved tubes bundle area; after heat convection, air temperature gradually falls and goes to front smoke box and turn to 3rd pass, which is smooth tubes bundle area, and then enters chimney passing back smoke box and exhausted to the atmosphere.
1. Digitized manufacture
The key part such as material cutting, rolling, drilling are proceeded by advanced CNC machining process to reduce the assemble stress and extend boiler working lifetime.
The front and back smoke chamber plates are cut by CNC plasma cutting machine and looks tidy and beautiful.
2.Easy operation and maintenance
Fully automatically operating, with automatically adjustment and protection of burning, water level, temperature and steam pressure.
3. Longer working life
Smoke tube and tube sheet connection is expanded first to eliminate the gap between them, then adopt automatic argon arc welding to relief the stress and expand boilers working life.
Longitudinal and girth joint adopt advanced automatic submerged-arc welding for good welding quality. All longitudinal and girth joint will have 100% radiographic inspection.
Fin tube us ND steel or stainless-steel material which avoid low temperature corrosion.
Inspection procedure point is set up to guarantee the sequence of expanding and welding, avoid cracking of the tube sheet holes.
4. Less fuel consumption
High quality aluminum silicate fiber is used with fire clay insulation, to control the boiler body temperature below 45℃ to control heat lost.
Sufficient steam storage room and heating area makes boiler to generate high quality steam and high thermal power.
Condenser is added to reuse the waste heat of the exhausted smoke to increase feeding water’s temperature and reduce emission temperature, which can increase the thermal efficiency above 98% and save operating cost.
The boiler is the part of the system that heats the water to be distributed. The key elements of a boiler include the burner, combustion chamber, heat exchanger, exhaust stack, and controls. Boiler accessories including the flue gas economizer are also commonly used as an effective method to recover heat from a boiler. Key Components of Boilers
Jan 15, 2019· Heat Transfer In Steam Boiler. A steam boiler is designed to absorb the maximum amount of heat released from the process of combustion. There are three way (Radiation, convection & Conduction) that heat is transfer in the boiler and relative percentage of each heat transfer within system boiler is dependent on the type of steam boiler, fuels and the designed transfer surface.
What is a water tube boiler? Water tube boilers were developed for a variety of reasons, including the need for higher steam pressures, higher steam generation rate, superheated steam. these types of boilers have quicker response to load changes. We briefly discuss about Water tube …
Water directly becomes steam. This is the Critical Pressure and the Critical Temperature. For steam this occurs at 374 deg C and 220.6 bar. Conventional steam power plants operate at a steam pressures in the range of 170 bar. These are Subcritical power plants. The new generation of power plants operate at pressures higher than the critical
Author: Learn Engineering CHAPTER 4 Steam power plants E. Khalil Department of Mechanical Power Engineering, Cairo University, Cairo, Egypt. Abstract The efﬁ cient utilization of fossil energy in power generation together with low pollution in conventional thermal power plants is a topic that is gaining interest internationally.
Inner Workings of a Combined-Cycle Power Plant. A combined-cycle power plant uses both a gas and a steam turbine together to produce up to 50 percent more electricity from the same fuel than a traditional simple-cycle plant. The waste heat from the gas turbine is routed to the nearby steam turbine, which generates extra power.
Steam power plant is a thermal power plant consists of main components and auxiliary components as well as other systems. The main component consists of four components, namely: - Boiler - Steam Turbine - Condenser - Generator. Boiler. Boiler has the function to convert water into steam. The process of change of water to vapor done by heating
Click to view4:22Aug 07, 2016· Auxiliary boiler of thermal power plant is used to produce initial steam (or other name is auxiliary steam) when the power plant startup. This steam used to reheat fuel oil, pipes and pray to
Steam Superheaters in Industrial Boilers. The Steam Superheater is a coil type heat exchanger which is used to produce superheated steam or to convert the wet steam to dry steam, generated by a boiler.. It is different from a boiler in a way that, boiler utilizes both sensible heat as well as latent heat to convert water into steam while superheater utilizes only sensible heat to superheat the
S. Laroche, in Steam Generators for Nuclear Power Plants, 2017. 184.108.40.206 Preheater thermal plate leakage. The integral preheater with crossflow usually includes a thermal plate that separates the feedwater from the recirculating flow from the downcomer flow entering the tube bundle. There is a small clearance gap between the tubes and the thermal plate and leakage is possible through this gap.
No. 76, Xin Da Road, Zhou tie Town, Yixing, Wuxi, China
0086-510-68530066, +86-13506151292Get Latest Price
Copyright © 2020.Zhongzheng Boiler Co., ltd. All rights reserved.