Product Thermal Capacity: 1 - 20 t/h
Working Pressure: 0.7 - 2 Mpa
Available Fuel: Nature gas, coke oven gas, biogas, methanol, liquid propane gas, diesel, heavy oil, light oil, crude oil, etc.
Available Industries: Heat supplying, chemical, food, textile, printing and dyeing, cigarettes and tobacco, fodder, pharmacy, building materials, brewery, rubber, hospital etc.
WNS series horizontal internal combustion boiler is a boiler shell type 3 passes wetback oil/gas fired boiler. After fuel is being atomized by burner, flame is full of the wave furnace and transfer heat via furnace wall, this is 1st pass; the high temperature smoke is collected in reversal chamber and then enters 2nd pass which is grooved tubes bundle area; after heat convection, air temperature gradually falls and goes to front smoke box and turn to 3rd pass, which is smooth tubes bundle area, and then enters chimney passing back smoke box and exhausted to the atmosphere.
1. Digitized manufacture
The key part such as material cutting, rolling, drilling are proceeded by advanced CNC machining process to reduce the assemble stress and extend boiler working lifetime.
The front and back smoke chamber plates are cut by CNC plasma cutting machine and looks tidy and beautiful.
2.Easy operation and maintenance
Fully automatically operating, with automatically adjustment and protection of burning, water level, temperature and steam pressure.
3. Longer working life
Smoke tube and tube sheet connection is expanded first to eliminate the gap between them, then adopt automatic argon arc welding to relief the stress and expand boilers working life.
Longitudinal and girth joint adopt advanced automatic submerged-arc welding for good welding quality. All longitudinal and girth joint will have 100% radiographic inspection.
Fin tube us ND steel or stainless-steel material which avoid low temperature corrosion.
Inspection procedure point is set up to guarantee the sequence of expanding and welding, avoid cracking of the tube sheet holes.
4. Less fuel consumption
High quality aluminum silicate fiber is used with fire clay insulation, to control the boiler body temperature below 45℃ to control heat lost.
Sufficient steam storage room and heating area makes boiler to generate high quality steam and high thermal power.
Condenser is added to reuse the waste heat of the exhausted smoke to increase feeding water’s temperature and reduce emission temperature, which can increase the thermal efficiency above 98% and save operating cost.
Nalco Company is the world's leading water treatment and process improvement company. We help our customers reduce energy, water and natural resource consumption, minimizing environmental releases while boosting the bottom line.
Nalco Water has helped thousands of customers globally with their boiler systems through automation, service, specialty chemistries, and equipment, to drive overall reduction of total cost of operation. We focus on customers in institutional, manufacturing, food & beverage, power generation, chemical, primary metals, paper, and mining.
Condensate returned to the boiler can positively impact water usage, energy and pretreatment costs. To realize the benefits of returning condensate, a programme of corrosion control must be implemented and maintained. Maximising condensate return requires a balance of …
Practical, up-to-date techniques for identifying and eliminating common causes of boiler failure. Filled with more than 200 color images, The Nalco Guide to Boiler Failure Analysis, Second Edition categorizes distinct failure modes that typify nearly all boiler problems and walks you, step by step, through their solutions. Each type of failure
Nalco Company. Nalco was founded as National Aluminate Corporation in 1928 through a merger of Chicago Chemical Company and Aluminate Sales Corporation, two Chicago-based companies selling sodium aluminate to treat water. Chicago Chemical Company sold mainly to municipalities and industrial plants for boiler feedwater treatment.
2/18/2014 3 Cheat Sheet - Reactions • Bicarbonate Break: Na 2 HCO 3 + HEAT Na 2 CO 3 + CO 2 + H 2 O • Developed Alkalinity: Na 2 CO 3 + HEAT + 2H 2 O 2NaOH + CO 2 + H 2 O • Brining Reactions: CaCl + Boiler Water CaSO 4 + CaSiO 3 • Phosphate Reactions: Ca 3 (PO 4) 2 Tricalcium Phosphate
Nalco 22310 is a Boiler water internal Treatment Chemical manufactured by Nalco Company . Its physical state is of a liquid that appears as yellow orange fluorescent. Nalco 22310 by nature has no odor and of specific gravity about 1.19 @ 77 øF / 25 øC.
Mar 19, 1997· Abstract of EP0640747 A pH/phosphate program in a boiler water system is controlled by: (1) determining the feed rate of the phosphate to the boiler by adding to a phosphate-feed s Login for instance under the trade names of Nalco 7208 and 7209 from Nalco Chemical Company of Naperville, Illinois. Phosphate feeds comprised of monosodium
nalco boiler water treatment : poly aluminium chloride msds English name : P oly A luminium Chloride /P AC Molecular formula: [AL2(OH)LnCL6-n]m Hs Code: 2827320000 CAS Code: 1327-41-9 Standard: GB15892-2003 Appearance : yellow powder Synonyms: PAC; Aluminum chlorohydrate; Aluminum chlorhydroxide; Aluminum chloride, basic; Aluminum hydroxychloride; Poly Aluminum Chloride; …
The Nalco Water Guide to Boiler Failure Analysis, Second Edition - Kindle edition by NALCO Chemical Company. Download it once and read it on your Kindle device, PC, phones or tablets. Use features like bookmarks, note taking and highlighting while reading The Nalco Water Guide to Boiler Failure Analysis, …
No. 76, Xin Da Road, Zhou tie Town, Yixing, Wuxi, China
0086-510-68530066, +86-13506151292Get Latest Price
Copyright © 2020.Zhongzheng Boiler Co., ltd. All rights reserved.