Product Thermal Capacity: 1 - 20 t/h
Working Pressure: 0.7 - 2 Mpa
Available Fuel: Nature gas, coke oven gas, biogas, methanol, liquid propane gas, diesel, heavy oil, light oil, crude oil, etc.
Available Industries: Heat supplying, chemical, food, textile, printing and dyeing, cigarettes and tobacco, fodder, pharmacy, building materials, brewery, rubber, hospital etc.
WNS series horizontal internal combustion boiler is a boiler shell type 3 passes wetback oil/gas fired boiler. After fuel is being atomized by burner, flame is full of the wave furnace and transfer heat via furnace wall, this is 1st pass; the high temperature smoke is collected in reversal chamber and then enters 2nd pass which is grooved tubes bundle area; after heat convection, air temperature gradually falls and goes to front smoke box and turn to 3rd pass, which is smooth tubes bundle area, and then enters chimney passing back smoke box and exhausted to the atmosphere.
1. Digitized manufacture
The key part such as material cutting, rolling, drilling are proceeded by advanced CNC machining process to reduce the assemble stress and extend boiler working lifetime.
The front and back smoke chamber plates are cut by CNC plasma cutting machine and looks tidy and beautiful.
2.Easy operation and maintenance
Fully automatically operating, with automatically adjustment and protection of burning, water level, temperature and steam pressure.
3. Longer working life
Smoke tube and tube sheet connection is expanded first to eliminate the gap between them, then adopt automatic argon arc welding to relief the stress and expand boilers working life.
Longitudinal and girth joint adopt advanced automatic submerged-arc welding for good welding quality. All longitudinal and girth joint will have 100% radiographic inspection.
Fin tube us ND steel or stainless-steel material which avoid low temperature corrosion.
Inspection procedure point is set up to guarantee the sequence of expanding and welding, avoid cracking of the tube sheet holes.
4. Less fuel consumption
High quality aluminum silicate fiber is used with fire clay insulation, to control the boiler body temperature below 45℃ to control heat lost.
Sufficient steam storage room and heating area makes boiler to generate high quality steam and high thermal power.
Condenser is added to reuse the waste heat of the exhausted smoke to increase feeding water’s temperature and reduce emission temperature, which can increase the thermal efficiency above 98% and save operating cost.
Mcdonnell & Miller 153927-LWCO - PSE802-24, Electronic 24V Low Water Cutoff with Auto Reset (Steam) - The Series PSE-800 probe type LWCO uses patented technology to monitor changes in water conductivity. When defined parameters are exceeded the new PSE-800 makes a decision to shut the burner off based on the volatility/variability of the resistance readings.
The needed repairs can range from, re-tubing to total destruction of the unit, if it is overheated. In the event of low water, the low water trips will trip the burner (or fuel flow for solid fuel boilers) and shut down the forced draft fan. This shuts down the heat input. A LOW-WATER CUTOFF IS A MAINTENANCE MUST!!!
The low water cutoff (LWCO) has a sensor - varying by the LWCO design - that has to be put into the boiler at a location that allows the sensor to detect the fall of boiler water below a "safe" level in the boiler.
The CycleGard LWCO should cut off the boiler 15 seconds after the boiler water level falls to below the LWCO sensor probe (that you can't see, it's behind the blue CycleGard control box and is inserted through a tapping into the steam boiler).
Oct 01, 2014· If your Weil McLain Gold water boiler has stopped working due to a low level water light being on, this video will show you how to clean the sensor. These tend …
Author: Donna Boyle Schwartz For accurate and dependable boiler protection, our Low Water Cutoff (LWCO) features the simplicity, reliability and unmatched quality you’ve come to expect from Taco Electronic Controls. The LWCO is a probe style, microprocessor based control that detects the fluid level in hot water and steam boilers.
User rating: 4.8/5 When water covers the probe, the RED “Low Water” LED on the control turns off. 3. Set the thermostat to call for heat and make sure that the burner ignites. 4. With the burner “on”, activate the test feature (“Testing the Low Water Cut Off” on page 6) while observing the burner and the “Low Water” LED on …
No. 76, Xin Da Road, Zhou tie Town, Yixing, Wuxi, China
0086-510-68530066, +86-13506151292Get Latest Price
Copyright © 2020.Zhongzheng Boiler Co., ltd. All rights reserved.